The Wi-DIT is a battery-operated digital counter and wireless temperature sensor with a microprocessor-controlled 418 MHz, FCC-certified radio transmitter and a digital input designed for use with our Wi-MGR.
The Wi-DIT provides a temperature output signal from an internal thermistor, a closed contact signal to the digital counter input, and the information is wirelessly transmitted to a point managing receiver (RLE’s Wi-MGR wireless sensor network manager). This architecture allows the Wi-DIT sensor to consume minimal power, resulting in a battery life of up to four years.
The Wi-DIT also accepts a normally open (NO) or normally closed (NC) dry contact signal.
If your unit is not working correctly, first check the battery.
- Make sure the sensor is equipped with a AA LITHIUM battery.
- Make sure the battery clips are clean and free of residue.
- Sometimes the clips get stretched out, so they don’t make proper contact with the battery. Squeeze the battery clips gently to ensure they are firmly touching both ends of the battery.
Consult the quick start guide for further installation and troubleshooting information.
Visit our support forum & join our community.
If you’ve read all the support documents and are still stuck, our forum should be your next stop.
Whether you search current content or submit a new topic for assistance or discussion, our in-house support staff and global user community are ready to help!Visit Our Forums
Need more help?
We’re here for you.
You’ve combed through the user guides and searched the forum, but you still can’t find the answers you’re looking for. Don’t worry – help is just a form submission away.
Complete our support request form and we’ll get back to you with expertise and answers within one business day.Request Product Support